Characteristics of the De Novo Data Center
The De Novo data center is divided into two physical blocks in which the processes and metrics specified in the contract differ.
DC–1 is the only data center in Ukraine built on a modular basis.
Each module is a physically limited volume, which consists of separate shielded cameras connected to the engineering infrastructure.
DС–5 is intended for placement of the equipment in the common space.
The engine room consists of the unshielded cameras connected to system of power supply of DC–1, zones of presence of telecom operators in DC–1 and dispatching system. All other systems are their own.
Comparison of DC–1 and DC–5
|November 2010||April 2018|
|Square||2117 m2||1200 m2|
|Electrical capacity||total 3050 kW|
|IT capacity||1050 kW||500 kW|
|Types of machine halls|
S - 4 racks / 30 kW
L - 8 racks / 60 kW
H - 25 racks / 160 kW
2 halls with 36 racks each/ 115 kW
2 halls with 34 racks each / 115 kW
|Machine halls shielding||The resolution of NBU №243||–|
|The raised floor limit of load||1500 kg||800 kg|
|The rack limit of capacity||≤ 15 kW power consumption||≤ 10 kW the total value of the power supplies installed on one shoulder.|
|The microclimate of machine halls||comply with ASHRAE|
2 inputs to the building, 2 telecom operator presence rooms
At least 15 telecom operators
|External electricity supply||2 TM-4000/10 kVA substations with power supply from Nivki substation and Priorskaya substation|
|Power Assemblies||АВВ MNS||Schneider Electric|
|Diesel generators||4 (3) (N+1) Cummins C1675 D5, 1340 кВт (Standby)|
|Fuel||5m3, 5m3, 1m3 main reservoirs, 5 м3 emergency tank|
|Uninterruptible power supplies|
2 rooms (N+1), 6 (4) MGE Galaxy 7000, 500 kVA
Operating time from the battery not less than 15 minutes
|Batteries||2 rooms (N+1), 6 (4) chains 144 pcs. YUASA SWL1800FR 55 Ah|
System chiller-fancoil (N +1)
5 (3) chillers Clivet WSAT-XSC 240H
2 hydro accumulator 40 m3, autonomy up to 40 minutes
73 air conditioner STULZ ASD 420 SW
6 (5) air conditioners STULZ ASD 800 SW
4 air conditioner APC InRow ACRC100
Precision air conditioners
4 x 4 (2) STULZ ASD 391 ASF
Citect SCADA software, Schneider Electric hardware
At least 29 000 controlled variables, at least 500 mimics
|Access control||APACS 3000, archive more than 200 days|
|The early fire detection system||SECURITON ASD 535||FMST-FXV-44E|
|Fire suppression||FIKE, extinguishing agent HFC-227еа||BGP Impulse-100-2 extinguishing agent HFC-125|
|Video surveillance||Over 120 cameras, archive more than 70 days||Over 50 cameras, archive more than 70 days|
|Support||24 / 7 / 365 according to SLA|
|Staff||At least 6 workers per shift|
Additional equipment according to the technical task
Implementation requires approvals
Products by the configurator
Quick activation period
* 4 (3) — design and the actual amount of installed equipment
Characteristics of Tier III-IV
- Component redundancy - N+1.
- Availability of services - 99.98%.
- Maximum allowed downtime - 1.6 hours per year. De Novo data center operates without a single shutdown during the whole period of its existence.
- Uninterrupted cooling.
- Two active resource allocation routes.
- Hot replacements for "vital" resources.
- The number of employees per shift: more than 2 engineers.
- Technical support in 24/7 mode.
- Allocation to screened dedicated modules.
Rent a secure module
|Square||14 m2||24 m2|
|Number of racks||4||8|
|Power quota for IT equipment||30 kW (40 kW - boost mode)||60 kW (80 kW - boost mode)|
|Maximum power density||20 kW / rack||15 kW / rack|
|Ability to install enterprise racks||yes|
|Power inputs||two independent|
|Topology of redundant precision cooling of IT equipment||universal: front → rear; bottom → top; front → top; front / bottom / rear → top|
|Load on the raised floor||1500 kg (distributed), 500 kg (point)|
|Cable communications||data center switching centers (2 pcs.) + intermodule communications (if necessary)|
|Screening||in accordance with the requirements of the resolution of the NBU №243 from 04.07.2007|
|Firefighting||Autonomous automatic gas, VESDA early detection system|
|Autonomous fire resistance||60 minutes|
Cabinet space rental
|Cabinet space rental in a shielded module||Cabinet space rental in the collective engine room||Rent ½ cabinets in the collective engine room|
|Rack type||width up to 800 mm, depth up to 1200 mm||width up to 800 mm, depth up to 1200 mm||width up to 600 mm, depth up to 1100 (1200) mm|
|Rack height||Up to 48 U||Up to 48 U||20 U|
|Maximum power density||≤ 15 kW / rack||≤ 10 kW / rack for power supplies||≤ 5 kW for power supplies|
|Power inputs||two independent|
|Topology of redundant precision cooling of IT equipment|
front → rear;
bottom → top;
front → top;
front / bottom / rear → top
|front → rear|
|Maximum rack weight||1500 kg||800 kg|
|Communications||data center switching centers (2 pcs.) + intermodule communications (if necessary)||data center switching centers (2 pcs.)|
Get an offer
De Novo Data Center offers a wide range of equipment placement services.
You can rent a rack or ½ rack in our Data Center.
For large companies and financial institutions, De Novo offers rental of individual shielded modules.
Fill out the form and describe the task, and our experts will offer you the best solution.
Are you interested in this page?
We care about the quality and relevance of our services and products, so your opinion is very important to us.